[an error occurred while processing this directive]
Posted by Dave on February 05, 2006 at 21:41:53:
In Reply to: Re: wiring boiler/ergomax in my situation posted by Heatpro on February 05, 2006 at 20:04:33:
: could I just have him put the return manifold on the top of the tank and the supply at the bottom?
: +++ It should do the trick.
Well, this spring, I'll have the plumber come back and pipe the supply manifold from the bottom of the tank and the return to the top.
As far as what we have now....I have the boiler pump running whenever any zone calls for heat. The boiler is just set to come on when the inlet temp is below about 160 and shut off at 175. Operation and Efficiency-wise, is this OK? The ergomax currently is not wired to the boiler. Wold the heatmanager work well in this situation until I get it repiped?
Post a Followup