[an error occurred while processing this directive]
Posted by Dave on February 06, 2006 at 12:24:23:
In Reply to: Re: wiring boiler/ergomax in my situation posted by HeatPro on February 06, 2006 at 11:09:02:
: Isn't that essentially what I have now? My I meant no disrespect and am more frustrated than anyone.
I did exactly what we had discussed ad infinitum and then we had an issue with the Phase III and all zones heating to boiler temp.
Nowhere that I can remember did we discuss balancing each zone separately, unless I completely misunderstood. Unfortunately, I am not a heating contractor. So when we were faced with 180 degree water coming from our hot water taps, I turned to the ergomax rep as i coyuld not get in touch in you.
In my haste to solve the problem, I listened to him even though I had also thought about simply switching the supply and return headers at the tank.
Now I am faced with going back a third time to my plumber who is going to think I am a schizophrenic when i tell him that I want the system repiped again. It is only probably a couple hours work. I just want to be sure that when we switch the supply and return headers on the tank that we have no other issues.
Again, I apologize for my ignorance, but I tried in very good faith to follow what was discussed here.
Post a Followup