[an error occurred while processing this directive]
Posted by Dave on May 05, 2006 at 16:57:56:
I had purchased the Issc 1081 timer to run my boiler circ for a minute or 2 after the call for heat ended to pull any excess heat from boiler heat exchanger to Ergomax
I spoke with the tech rep this morning and he had said to apply 120 v input power to terminals 7 and 2.
He then said I should wire the pump (120 V)to NO terminals 6 and 8.
Before I hooked the pump to it, I used my voltage tester, and that does not make sense. I get no power anywhere except between terminals 7 and 2.
Here is the datasheet:
I was going to take the hot wire from the boiler and attach to 7 and neutral from boiler to 2. THen hot wire to pump on 6 and neutral to pump on 8.
Would you be able to tell me how it should be wires? Technical is closed until Monday.
Post a Followup