[an error occurred while processing this directive]
Posted by Dave on May 05, 2006 at 17:57:54:
In Reply to: wiring of off-delay timer posted by Dave on May 05, 2006 at 16:57:56:
Actually, looking at the diagram a little closer, this is what i did:
*I wired power to the timer across 7 and 2
*I left the neutral wire to the pump where it originally was (secured to neutral wire from boiler.
*I ran hot wire from boiler to terminal 3
*Hot wire to pump at terminal 1
When the system is running, the pump runs, but as soon as the boiler shuts off, so does the pump. (there is no off-delay).
Post a Followup