[an error occurred while processing this directive]
Posted by Dave on May 03, 2006 at 20:41:23:
In Reply to: Re: question regarding Ergomax repipe posted by HeatPro on May 03, 2006 at 17:46:20:
So his reason for making the cross-section 1/4 the size is to correct a possible restriction elsewhere.
+++I don't understand the above statement. Would the scenario I gave for piping to the PRV and Temp gauge inlets work without undue restriction if all 007 pumps were running at once?
His concern with piping the return header to the boiler supply to the Ergomax is that the 0010 would overwhelm the 007's and restrict flow into the tank.
Post a Followup