[an error occurred while processing this directive]
Posted by Dave on December 01, 2005 at 23:04:06:
In Reply to: Re: Change in my repiping/buffer tank schedule posted by HeatPro on December 01, 2005 at 22:14:57:
The supply manifold stub where all the zone tees branch to the zones and the return manifold stub would be removed from the manifold and the manifold used for some piping or discarded. Yes, It is the normal operation of a multizone system manifold off a boiler
+++so to clarify, you are saying to pipe that vertical 1.5" pipe that is currently attached to the tee into the top of the tank.
Would the 1.5" return manifold pipe and boiler inlet pipe be teed right at the tank?
Yes, on a 2-inch tee.
+++It would be a tee that is 2" with a 1.5 " connection on top for return. That won't be a flow issue when both the boiler circ and return zones are running all through the tee?
As far as the Spirovent, etc I was just going to have the plumber get an actual Spirovent by Spirotherm.
Do you have any recommendations on exactly what to get for this application?
Post a Followup