[an error occurred while processing this directive]
Posted by HeatPro on June 15, 2009 at 09:56:05:
In Reply to: Boiler for a small heat load posted by Grinch on June 15, 2009 at 00:32:41:
Yes, the burner will turn on and off as most do without being able to modulate to keep it running long.
Add a tank as here:
and you can make hot water and heat without any such concerns.
Add more baseboard to have the system average water temp kept below 140F and you can use a condensing boiler to gain the maximum fuel savings.
Post a Followup