[an error occurred while processing this directive]
Posted by rbeck on November 30, 2008 at 07:37:02:
In Reply to: Re: New Burnham boiler cycling posted by HeatPro on November 29, 2008 at 17:52:35:
Steam boilers are sized by connected load only. Do a connected load calculation and match thsat to the sq. ft. steam on the boiler. DO NOT ADD ANYTHING to that number. Manufactureres already deduct 33% for the piping.
If the IN8 is natural gas it might be able to be reduced by 20%. If it is LP it cannot be reduced.
Post a Followup