[an error occurred while processing this directive]
Posted by jeremiah on September 02, 2008 at 20:03:42:
In Reply to: Re: larger to smaller pipes posted by HeatPro on September 02, 2008 at 18:36:59:
With 4 gpm, is this about the basic piping?
With a low loss, is this close to correct?
: The heat loss of the home is about 40,200 btu/hr.
: OK, that translates to your needing 4 gpm. The boiler will modulate down to that need as the circulator takes water through at that rate.
: How can I calculate how much radiation is throwing off heat?
: +++ Tell whether it is baseboard or radiators and read:
Post a Followup