[an error occurred while processing this directive]
Posted by HeatPro on September 02, 2008 at 18:36:59:
In Reply to: Re: larger to smaller pipes posted by jeremiah on September 02, 2008 at 15:36:43:
The heat loss of the home is about 40,200 btu/hr.
OK, that translates to your needing 4 gpm. The boiler will modulate down to that need as the circulator takes water through at that rate.
How can I calculate how much radiation is throwing off heat?
+++ Tell whether it is baseboard or radiators and read:
Post a Followup