[an error occurred while processing this directive]
Posted by jeremiah on September 02, 2008 at 21:56:10:
In Reply to: Re: larger to smaller pipes posted by HeatPro on September 02, 2008 at 20:46:35:
Okay, here's a new basic setup for you to look at for me. You're a great teacher and aid.
I don't need the system to do very many gpm, so would this pump be adequate to pump into the boiler?
: : With 4 gpm, is this about the basic piping?
: : http://i479.photobucket.com/albums/rr151/jeremiahjm/boilerwithoutlowloss.jpg
: +++ No to the above, as Wiessman recommends the following, it is wise to do as the manufacturer says and use the low loss header.
: : With a low loss, is this close to correct?
: +++ Yes, as it is recommended by Viessman.
: : http://s479.photobucket.com/albums/rr151/jeremiahjm/?action=view¤t=pipinglayout1.jpg
Post a Followup