[an error occurred while processing this directive]
Posted by HeatPro on July 30, 2008 at 20:33:35:
In Reply to: Warden King boiler posted by Don on July 30, 2008 at 19:32:40:
Pay attention to the system pressure, kettling can often be stopped by raising the pressure some pounds and/or increasing water flow with a pump that can move more water. Having multiple zones can slow water flow when some zones are closed, A bypass pipe, so water can flow faster through the boiler can stop the kettling then.
Post a Followup