[an error occurred while processing this directive]
Posted by HeatPro on September 18, 2006 at 20:08:40:
In Reply to: Re: Wiring Honeywell V8043E with taco 007 and Honeywell RA832A Relay posted by chris on September 18, 2006 at 18:50:33:
Yes, you've become confused and diverted by getting a zone circulator relay SR501. You now have a spare RA832 to decorate the house, as the SR501 does the same as the RA832. in the instructions I gave above.
The red wires of the zone valve now go to RW otherwise known as the TT.
A ZVC403 three-zone-valve control would have been what you needed to simplify the matter.
Post a Followup