[an error occurred while processing this directive]
Posted by HeatPro on July 30, 2006 at 23:35:59:
In Reply to: Re: Follow directions if possible posted by Ruth on July 30, 2006 at 22:43:57:
MAIN POINT OF KNOWLEDGE: The 'pump-away' rule NEVER puts the expansion tank on return piping, so the basic requirement is to know what 'pump-away' means.
SECOND POINT: The instructions found at:
has a NOTE in bold type on page 16 saying: "Never install expansion tank and auto-fill valve on the return."
Right after that note, 7. says "If necessary, install a properly sized circulator with optional isolation valves in supply beyond expansion tank.
Therefore, the instructions to READ THE INSTALLATION MANUAL is a good idea.
Post a Followup