[an error occurred while processing this directive]
Posted by Ruth on July 31, 2006 at 14:10:11:
In Reply to: Re: Follow directions if possible posted by HeatPro on July 31, 2006 at 13:03:00:
Actually we do have an external circulator installed on supply. But for some unknown reason the installer switched it off and told me never touch it, which is another mystery he left. I will try to push him to re-pipe the system as you suggested. Thanks a lot.
: In other words, no matter whether you use their diagram which is the BEST way to do it, or you allow the system to be piped as an often-used in-line series piping method, you still wind up with two circulators. So you may as well have the system repiped to how the factory instructions say - to the loop-subloop according to their drawings.
Post a Followup