[an error occurred while processing this directive]
Posted by joe on May 19, 2006 at 09:57:29:
In Reply to: Re: Gas Steam Boiler posted by Heatpro on May 18, 2006 at 13:53:33:
Heatpro I don't see the chart 7 at
I also have two more questions:
(1) are monoflow tees used with the European two pipe system? (For my system I'll have 1" supply and return piping with 3/4" risers, for a total of 4 zones requiring a total of 60K BTU)
(2) Can I use a simple 3/4" ball valve (with the lever handle) as a balancing valve?
(3) Where does the balancing valve get placed, on the branch between the radiator and supply line, or the branch between the radiator and return line.
Post a Followup