[an error occurred while processing this directive]
Posted by Dave on January 18, 2006 at 11:34:35:
In Reply to: Re: Ergomax and boiler wiring and settings posted by HeatPro on January 18, 2006 at 11:06:01:
OK. I'm just a little confused. In my Taco SR504 controller, I would attach the wire for the burner control (24 v) in parallel with the first floor fan coil as this is the largest zone. Currently, the boiler pump is wired directly into the boiler circuitry, so when the boiler comes on, so does the pump. I assume I'd leave that the same.
I would also hook up the Ergomax aquastat to the same connection in the relay panel. Are you saying to use the low voltage wires for the ergomax where the thermostat wires for my first floor fan coil are attached?
Let's remove the outdoor reset from the equation for a moment as I won't have that for a while.
Could you just go over exactly what needs to be connected where?
Post a Followup