[an error occurred while processing this directive]
Posted by Heatpro on January 18, 2006 at 15:16:05:
In Reply to: Re: Ergomax and boiler wiring and settings posted by Dave on January 18, 2006 at 12:49:43:
Ah, yes ... the eternal yeah-but as information comes in. We talked as if there were individual circulators all year.
You've got a problem with the SR504 as there is no direct control of individual circulators without the burner and boiler circulator running. The easiest way to avoid the problem is to put the T475A outdoor reset or a Beckett Heatmanager in now and not worry about inventing patches for the problem.
Post a Followup