[an error occurred while processing this directive]
Posted by mike on September 25, 2009 at 22:16:34:
In Reply to: Re: Pressuretrol Honeywell PA404a posted by HeatPro on September 23, 2009 at 09:46:14:
: You might not have a problem. Your heat reached 75F and the burner shut off. Guages aren't all that accurate and just a few ounces of steam pressure can do the job. As it ran for 30 minutes, your boiler burner isn't oversized. You have no banging nor clanking. With close temperatures inside and out, your thermostat won't be accurate until the weather demands more run time.
: As the weather gets colder, check to see that all radiators are getting warm so the vents are set to make an even heat in every room.
I changed the gauge and the pressuretrol All seems to be working well.. Cut out 2Psi and cut in at .5. I'm comming out of the summer and getting ready for the fall. I noticed that one sunrad all of a sudden stopped working? Is it the vent? It looks OK but it might not be. Could It be anything else?
Post a Followup