[an error occurred while processing this directive]
Posted by Dan on April 24, 2009 at 10:25:10:
In Reply to: Re: relatively new relief valve dripping posted by tk03 on April 24, 2009 at 09:26:56:
: Sorry I thought it was the domestic side. If there is a working relief valve on the boiler and there is nothing blocking the expansion from the tank to the boiler one relief valve is OK.
Thanks. That's what I had thought. Since the boiler only runs to 180 and has its own relief valve, I couldn't figure how this would ever be an issue with the tank, especially since the tank is rated to 150 psi.
Post a Followup