[an error occurred while processing this directive]
Posted by Doug Criner on December 05, 2008 at 18:45:52:
In Reply to: Boiler Won't Fire posted by JS on December 05, 2008 at 16:10:31:
Two possiblities: the gas valve is sticking or the milivolt generator isn't putting out enough voltage to open the valve. If you have a digital voltmeter, see what voltage you are getting at the valve - not sure of specs, but probably a few hundred millivolts.
I doubt that your turning off the pilot for the summer caused your problem.
Post a Followup