[an error occurred while processing this directive]
Posted by rbeck on November 02, 2008 at 18:52:54:
In Reply to: Re: Low water cycle problem? posted by HeatPro on November 01, 2008 at 19:18:52:
You are surging. This is normal after a steam boiler installation. There is oil on top of the boiler water. It needs skimmed.It could be a few other things but normally skimmed. Could also be a piping issue.
See these links
Post a Followup