[an error occurred while processing this directive]
Posted by HeatPro on May 27, 2008 at 18:48:07:
In Reply to: Honeywell Aquastat 8124C adjustment for Cold Start posted by jxsori on May 27, 2008 at 15:44:14:
Pulling the blue wire that is inserted into the hole just below the low limit, wire-nutting and taping it so it doesn't touch, disables the burner from firing to maintain the low limit temperature, which makes the 8124 similar to the cold start 8148.
Post a Followup