[an error occurred while processing this directive]
Posted by Heatpro on January 18, 2006 at 22:26:53:
In Reply to: Violent Banging/Water Refill posted by Scott on January 18, 2006 at 18:46:38:
No, a new boiler shouldn't lose that much water without a leak.
Your problem might be a misplaced Hartford Loop, as a new boiler and the old aren't usually the same height nor water-line. See the installation sheet for the height.
Alse, make sure the pressure is right, the pipes are sloped properly and the radiators didn't sag nor have closed or the wrong valves - per instructions here:
Post a Followup