[an error occurred while processing this directive]
Posted by Dave on November 30, 2005 at 15:02:32:
In Reply to: Re: To HeatPro and Joe Brix posted by HeatPro on November 30, 2005 at 14:43:02:
OK. I will order the RJS080, which is their 80 gallon tank. It has a 2" hot water outlet at the top and two 2" connections on the lower side, as well as a 3/4" drain and a 1" T&P port near the top.
I guess the hot boiler water would be piped into one of the lower 2" connections and then exit out the 2" connection at the top. Then we would just cap the other 2" connection as well as the 1" T&P port?
It will take awhile to get the tank, and the plumber really wants to redo the primary loop first, so what we were thinking was he would pipe 2 2" tees into the boiler outflow pipe with a shutoff valve between. The tees would be capped until we get the storage tank. Then he would pipe in the tank to those tees, and we would turn off the shutoff so the boiler water would be forced to go through the tank. Does that all sound OK?
Post a Followup