[an error occurred while processing this directive]
Posted by HeatPro on November 16, 2005 at 19:08:37:
In Reply to: Re: Getting boiler to operate more efficiently posted by Justin on November 16, 2005 at 17:35:55:
Look for another tapping in a section to insert the outdoor reset sensor into a well, add a well into a tee right off the boiler top supply pipe, or set the sensor right on the casting under the jacket. A remote sensor is a problem.
Post a Followup