[an error occurred while processing this directive]
Posted by Harold hydronicnetwork.net on January 27, 2004 at 08:15:01:
In Reply to: Baseboard not getting enough heat posted by Holly L on January 27, 2004 at 07:15:25:
The tee off your main line is most likely a diverter fitting already. The problem is more likely to be due to air being trapped and not getting out, so look for a little valve at one of the elbows at the end of the baseboard upstairs to vent some air. If the baseboard ever worked in the past, it will again if more water of the right temperature can get through again.
Post a Followup