[an error occurred while processing this directive]
Posted by Harold hydronicnetwork.net on January 21, 2004 at 08:38:33:
In Reply to: REpost aquastat posted by adp on January 21, 2004 at 08:13:32:
A more important question is why the high limit is set at 180F and the low limit is set at 160F. That is 20F difference, so a differential of 25F on some particular controls will not work well, and might work well on another brand, if there is a purpose in all that. Giving blanket answers that will not fit some situations is not intelligent. Provide information as to whether this is a tankless coil boiler or not and why the high limit is set that low. the low limit set there, as well as the aquastat model number.
Post a Followup