[an error occurred while processing this directive]
Posted by adp on January 21, 2004 at 09:38:03:
In Reply to: Re: RE aquastat settings posted by Harold hydronicnetwork.net on January 21, 2004 at 09:15:20:
: Traditional settings for a hot water coil is 210F high, 180F low with a 20F differential.
: If your hot water has been enough, then leaving the settings where they are and a 20F differential could keep the water OK.
: If you move the settings higher (or even if not) make sure you have a tempering valve to help prevent scalds.
THANK YOU ONCE AGAIN FOR YOUR HELP.....
Post a Followup