[an error occurred while processing this directive]
Posted by Harold hydronicnetwork.net on December 28, 2003 at 18:07:21:
In Reply to: steam radiator (1-pipe system) suddenly stops heating if you leave the steam valve on? posted by ken on December 28, 2003 at 15:43:26:
Try a different brand steam vent. First swap the vent on a radiator that is working well with the bad vent to see what happens. The opening and closing of the valve with the vent on and off proves that the radiator heats OK if the vent would work OK.
Post a Followup