[an error occurred while processing this directive]
Posted by JoeW on June 14, 2011 at 12:47:10:
In Reply to: Re: Boiler sizing Measured radiators posted by JoeW@ on June 13, 2011 at 21:46:17:
: : You can read the EDR from these tables:
: : http://www.ecrinternational.com/secure/upload/document/293.pdf
: Thanks I now have the EDR for each radiator. Do I understand I now Multiply each sq./ft edr x 240btu/hr///// then add all the sums together to get the total radiation heating demand on the boiler?
Thanks for your help. My total sq/ft of steam came in at 220.
Cross reference with Starfire boilers shows Model SFE 365S rated at 246sq/ft steam, That is going to be the choice.
Post a Followup