[an error occurred while processing this directive]
Posted by tk03 on February 06, 2010 at 08:29:33:
In Reply to: Re: weil mclain ultra posted by HeatPro on February 04, 2010 at 15:22:34:
What type of glycol are you using. It takes a special glycol for aluminum heat exchangers. Alumax is a good one but get the wallet out. If the glycol used is standard glycol it cannot be used.
Weil has taken a beating on this but it is not their fault. They specify glycol for aluminum.
Post a Followup