[an error occurred while processing this directive]
Posted by Jeff on October 04, 2009 at 15:35:07:
In Reply to: Re: Sludge in sight glass and in valve below posted by Jeff on September 28, 2009 at 19:21:58:
Cleaned it out and flushed it through lower valve of the sight glass (glass removed of course). until it ran clear. Put it back together, filled to the fill line, and turn it on. Seems to be working well. I think the biggest issue is that it was never maintained properly, thus all the sludge. Hopefully by flushing it out it will operate more effectively. $400-$500 gas bills were killing me last December - March. I also replaced all the blow offs on all the radiators. Is there anything else I can do to help with efficiency?
Post a Followup