[an error occurred while processing this directive]
Posted by rbeck on October 09, 2008 at 22:26:33:
In Reply to: Burnham Mega Steam install? posted by Billy on October 08, 2008 at 21:13:03:
That would be the proper boiler sie. Measure all the radiation in sq ft of steam as you did and size the boiler from that. Do not add anything else. If the mains in the basement are not all insulated insulate them. Here is a lot of steam info you may find helpful.
See Steam FAQ and Boiler piping do's and don'ts. http://www.comfort-calc.net/tech_area_index.htm
Post a Followup