[an error occurred while processing this directive]
Posted by HeatPro on September 09, 2008 at 11:52:08:
In Reply to: Maximum loop for a Taco 0010 Pump posted by BillH on September 07, 2008 at 19:24:09:
: We have a 1850 sq. ft. ranch in PA with a Taco 0010 pump on a Weil-McClain boiler. The circuit is approximately 235 feet and we lose 50-60 degrees between the supply and the return. I saw that the max for a Taco 007 would be 100 feet for 50,000 BTUs. What is the maximum loop for the Taco 0010? Any help would be appreciated.
+++ the pumping ability isn't isolated from the gpm and the pipe size, you have to give them also to get an answer.
With either pump, you can but move 3.5 gpm which can give you 100,000 btuh at a 60 degree drop or
35,000 btuh with a 20 degree drop.
Post a Followup