[an error occurred while processing this directive]
Posted by jeremiah on September 02, 2008 at 16:06:49:
In Reply to: Re: larger to smaller pipes posted by jeremiah on September 02, 2008 at 15:19:32:
If I could edit these posts I would... according to the information found here... http://www.crownboiler.com/educate/sizeheat.asp...
the existing radiator elements are just over 100,000 btus. Is that an answer to the right question? ha.
: Alright, first things first I guess, sorry. The heat loss of the home is about 40,200 btu/hr. How can I calculate how much radiation is throwing off heat? Any resources for that?
: Thanks for all your prompt responses.
: : You are missing the important point:
: : WHAT IS THE HEAT LOSS of the house?
: : HOW MUCH RADIATION is throwing off heat?
: : You start from there for GPM.
: : Then you look at the buffer tank or low-resistance manifold piping,
: : which is boiler pipe from buffer tank or low-resistance manifold to boiler,
: : buffer tank or low-resistance manifold pipe to boiler with pump in it
: : - pipe from buffer tank or low-resistance manifold to radiation with pump and expansion tank in it
: : - pipe from radiation to buffer tank or low-resistance manifold.
Post a Followup