[an error occurred while processing this directive]
Posted by Heatpro on July 16, 2008 at 14:33:10:
In Reply to: Laars Endurance EBP-175 posted by Nick on July 16, 2008 at 13:50:46:
That is higher than necessary for hot water. The problem is common on models for a decade, having to do with sensor location and hot water reaching the top of the storage tank. Their web site gives directions in their installation and operation manual to replace the switch if it has tripped before 230F.
Page 33 on ...
Post a Followup