[an error occurred while processing this directive]
Posted by HeatPro on March 20, 2008 at 15:01:38:
In Reply to: peerless pinnacle pi-140-lp posted by wayne goodrich on March 19, 2008 at 10:51:29:
Low-water-volume, low-metal-mass boilers can have the problem when there is a delay in pumping rates to take the hot water out of the boiler. Find out if there are closed zone valves at the start. Low water flow can cause sizzling and banging. A minimum-flow bypass or loop-subloop system can eliminate the problem.
Post a Followup