[an error occurred while processing this directive]
Posted by Kyle on January 27, 2007 at 16:56:55:
In Reply to: radiant floor posted by cooper on January 24, 2007 at 12:28:07:
the only thing that i would lean towards is if your piping systen will allow to properly remove all the air from the pex on start up and after any repairs. It is better to be able to shut off each loop one at a time for better purge. I also would install a bypass around your water feed valve to allow for city water pressure during purge.
Post a Followup