[an error occurred while processing this directive]
Posted by HeatPro on October 25, 2006 at 15:10:00:
In Reply to: Re: Burnham Revolution Circulator Location posted by Ryan Smith on October 25, 2006 at 13:07:48:
It would be better to declare how you have the boiler pipe to the main.
Check off one:
A. The main from the radiation goes to the inlet of the boiler and the outlet of the boiler goes out to the radiation.
B. The returns from the radiation are tied directly to the main that goes to the radiation AND the boiler supply and return tie into the main on tees in the main about a foot apart.
If A, then the Grundfos isn't working.
If B, there should be ANOTHER circulator in one of the pipes going to or from the boiler.
Post a Followup