[an error occurred while processing this directive]
Posted by Rocco on February 25, 2004 at 20:15:42:
In Reply to: Re: venting boiler and water heater posted by Harold hydronicnetwork.net on February 25, 2004 at 20:10:19:
: A 30-foot high B-vent chimney serving two or more natural vent appliances with a 3-foot rise can handle 178,000 btuh; with interpolation for 5 more feet, it can handle the total.
: (National Fuel Gas Code)
That was fast. Thanks for your response. Now let me measure the actual chimney height and see if its in the right range.
Post a Followup