[an error occurred while processing this directive]
Posted by Harold hydronicnetwork.net on February 25, 2004 at 20:10:19:
In Reply to: venting boiler and water heater posted by Rocco on February 25, 2004 at 19:49:23:
A 30-foot high B-vent chimney serving two or more natural vent appliances with a 3-foot rise can handle 178,000 btuh; with interpolation for 5 more feet, it can handle the total.
(National Fuel Gas Code)
Post a Followup