[an error occurred while processing this directive]
Posted by George Walsh on February 17, 2004 at 16:16:49:
This is a new Lennox (Dunkirk) gas steam boiler on ancient piping.
Simplest first: I have the pressuretrol set at 2 with a 1 differential. System is quiet and steam is clean. But gauge on boiler never reads above .5. Is that correct?
Next: Should the pigtail feel hot right up to the pressuretrol? It doesn't. I cleaned a lot of gunk (balls of oil, lint, corrosion) out of this system by skimming and draining since November. Should I have a pro check pigtail?
Now the big one: Three radiators were re-piped during a renovation. Pipe size was reduced in process. Two small rads upstairs (one a short run, one long) do not heat unless I turn off a large one on first floor. I believe condensate may be trapped in two upstairs, but system pushes through it when large rad is off. Does this make sense? All three are on same main. I replaced main vents on the two existing mains and get great heat everywhere else. Should one or another of the rads that were repiped be piped off the second main?
Sorry for the complex questions...you guys are great.
Post a Followup