[an error occurred while processing this directive]
Posted by Heatpro on December 06, 2005 at 14:28:42:
In Reply to: Re: results of temperature experiment and Phase III posted by Dave on December 06, 2005 at 13:57:10:
(Just to get the language accurate, the flow controls at the circulator outlets are also check valves.)
Yes, set the Ergomax at 150F. Take Lochinvar at their word and let the tank control the water from 140F with a 10F differential. You can widen that to 140F-155F if necessary.
Yes, let the Ergomax feed the domestic water inside the copper tubes to the Phase III storage, then to the house.
Post a Followup