[an error occurred while processing this directive]
Posted by HeatPro on December 06, 2005 at 15:25:54:
In Reply to: Re: results of temperature experiment and Phase III posted by Dave on December 06, 2005 at 14:38:36:
: And the teed connections at the tank that I had in my previous post is OK? Yes
An option is to take the pumped pipes to the Phase III off the system manifold stubs; then tee at the Ergomax to use boiler water for both from a parallel manifold and get rid of another 007 circulator, flow control, and relay.
: Also, if the water for DHW is preheated by the Ergomax to 150, will the Phase III ever call for heat? Will that mean that our DHW will now be 150 degrees? Depends on the draw amount. The flow rate through the Ergomax determines if the Phase III gets 150 water or less. Having a tempering valve at the phase III determines if you get the boiler temperature or less.
Post a Followup