[an error occurred while processing this directive]
Posted by Jim on November 26, 2005 at 17:54:03:
I would like to add a buffer tank to my system. Would it be OK to put the supply and return of the buffer tank in the boiler loop on the output side of the boiler? I was thinking of placing the buffer tank tees next to each other just beyond where the main boiler pipe comes out of the boiler. This would allow the least amount of repiping.Then I would have a dedicated pump for the buffer tank that would only run when the heating zones are calling for heat, but would remain off when the indirect was calling for DHW.
Are there any potential problems/issues with the way I'd like to pipe this?
Post a Followup