[an error occurred while processing this directive]
Posted by Dave on October 18, 2005 at 19:35:45:
In Reply to: Re: What is correct sizing for boiler loop pump? posted by Joe Brix on October 07, 2005 at 11:50:27:
I'm starting to think about just adding a Tekmar controller so the high fire will only fire when the outddor temp is below a certain point.
The 261 would be the one I would like to get, but we also have a loop for the indirect (Phase III) for domestic hot water. Does that mean that we have to get the 262 which is double the price of the 261?
Our Taco relay board has a switch for priority for the DHW, but it is currently turned off. However, it would take me 2 secs to turn that switch on. Would that then allow me to use the Tekmar 261?
Post a Followup