[an error occurred while processing this directive]
Posted by HeatPro on August 15, 2005 at 22:54:00:
In Reply to: Re: pex sizing to kompak registers posted by Equinox Builders, LLC on August 15, 2005 at 22:35:17:
It would be simpler to run a 3/4-inch feed to the mid-point of the btuh of the lower floor, cut the tube at that point and tee to let the water flow in both directions from that point using the existing 1/2-inch pex. You would take the original supply side tube of the circuit and reconnect it to the return near the present 1st floor return on the return manifold.
Post a Followup