[an error occurred while processing this directive]
Posted by HeatPro on August 15, 2005 at 22:44:47:
In Reply to: Re: pex sizing to kompak registers posted by Equinox Builders, LLC on August 15, 2005 at 22:35:17:
be careful with the toekick, they usually use up to 4 ft of head or about 1/3rd of the pumping power, so it shortens the allowable length of 3/4 circuit by 1/3rd.
Post a Followup