[an error occurred while processing this directive]
Posted by Gary on January 25, 2004 at 09:33:38:
In Reply to: Re: one pipe steam vent controls- water trapped posted by Harold hydronicnetwork.net on January 25, 2004 at 09:19:26:
: The flow restrictor upstairs explains a lot. The pressure should be regulated down by the pressure control downstairs. A flow restictor upstairs creates an unnecessary and 'false' condition where steam constantly flows upward at an excessive rate to keep condensate up in the sytem instead of letting it fall back to the boiler.
Should I tell my heating service person to look into the pressure control at the boiler? He's been servicing the system for years.
Post a Followup